Updated: Nov 12
Adams received a call about some exposed and burnt wiring in a lounge light fitting.
The electrician went to the site and found the light fitting was old and had overheated, which had burnt and exposed the wiring. New light fittings were supplied and installed to the customer's satisfaction, and potential fire hazard was averted.
Problem solving easily.